The 1Home Bridge device setup consists of two steps: installation and pairing.
There are two different ways how 1Home Bridge can be installed:
Once the device is installed, you continue with Step 2 in the 1Home dashboard:
2. Pairing the 1Home Bridge with the 1Home dashboard
1.1. Direct KNX bus connection
The 1Home Bridge should be DIN rail mounted into your electrical cabinet and connected to a KNX bus cable via KNX module on the device, to an external 12-30 V DC power supply, and to the network via ethernet cable.
ETS Programming (optional)
You can assign the physical KNX address, set up BAOS username/password, and enable/disable various services using ETS. This step is optional and the device also functions using the default settings on the default Individual address 15.15.255.
Note: HERE you can find the ETS catalog if you want to program the 1Home Bridge in ETS.
1.2. Connection via a separate KNX IP Interface, Gira HomeServer, or Loxone Miniserver
Plug & Play extension
In a retrofit installation, the device doesn’t need to be connected directly to the KNX bus. This allows for a seamless retrofit to existing smart home infrastructure. You can simply install the device via the PoE adapter and keep it in the cabinet next to your router.
2. Pairing 1Home Bridge with the 1Home dashboard
Please visit bridge.1home.io and if you have already completed the installation process - simply skip the tutorial to Step 3 in the 1Home dashboard.
In the instructions that came with the device, there is a 10-digit code. Please enter the code in the 1Home dashboard. Your device should now be paired with the 1Home dashboard.
Once the device is installed - proceed with the configuration in the 1Home dashboard. See the instructions below.
If you'd like to program the 1Home Bridge in ETS 5, you can download the Catalogue HERE.
Do you have any questions or suggestions?
Please contact us via the chat button in the bottom right corner.